A settler is a primary treatment technology for wastewater; it is designed to remove suspended solids by sedimentation. It may also be referred to as a sedimentation or settling basin/tank, or clarifier. The low flow velocity in a settler allows settleable particles to sink to the bottom, while constituents lighter than water float to the surface.
Sedimentation is also used for the removal of grit (see pretreatement technologies), for secondary clarification in activated sludge treatment (see activated sludge), after chemical coagulation/precipitation, or for sludge thickening. This technology information sheet discusses the use of settlers as primary clarifiers, which are typically installed after a pretreatement technology
Settlers can achieve a significant initial reduction in suspended solids (50-70% removal) and organic material (20-40% BOD removal) and ensure that these constituents do not impair subsequent treatment processes.
Settlers may take a variety of forms, sometimes fulfilling additional functions. They can be independent tanks or integrated into combined treatment units. Several other technologies in this Compendium have a primary sedimentation function or include a compartment for primary settling:
o the anaerobic baffled reactor and the anaerobic filter both usually include a settler as the first compartment. However, the settler may also be built separately, e.g., in municipal treatment plants or in the case of prefabricated, modular units.
o the Imhoff tank and the upflow anaerobic sludge blanket reactor, designed for the digestion of the settled sludge, prevent gases or sludge particles in the lower section from entering/returning to the upper section.
o the solids-free sewer, which includes interceptor tanks at the building level.
The main purpose of a settler is to facilitate sedimentation by reducing the velocity and turbulence of the wastewater stream. Settlers are circular or rectangular tanks that are typically designed for a hydraulic retention time of 1.5-2.5 h. Less time is needed if the BOD level should not be too low for the following biological step. The tank should be designed to ensure satisfactory performance at peak flow. In order to prevent eddy currents and short-circuiting, as well as to retain scum inside the basin, a good inlet and outlet construction with an efficient distribution and collection system (baffles, weirs or T-shaped pipes) is important.
Depending on the design, desludging can be done using a hand pump, airlift, vacuum pump, or by gravity using a bottom outlet. Large primary clarifiers are often equipped with mechanical collectors that continually scrape the settled solids towards a sludge hopper in the base of the tank, from where it is pumped to sludge treatment facilities. A sufficiently sloped tank bottom facilitates sludge removal. Scum removal can also be done either manually or by a collection mechanism.
The efficiency of the primary settler depends on factors like wastewater characteristics, retention time and sludge withdrawal rate. It may be reduced by wind-induced circulation, thermal convection and density currents due to temperature differentials, and, in hot climates, thermal stratification. These phenomena can lead to short-circuiting.
Several possibilities exist to enhance the performance of Settlers. Examples include the installation of inclined plates (lamellae) and tubes, which increases the settling area, or the use of chemical coagulants.
The choice of a technology to settle the solids is governed by the size and type of the installation, the wastewater strength, the management capacities and the desirability of an anaerobic process, with or without biogas production.
Technologies that already include some type of primary sedimentation (listed above) do not need a separate settler. Many treatment technologies, however, require preliminary removal of solids in order to function properly. Although the installation of a primary sedimentation tank is often omitted in small activated sludge plants, it is of particular importance for technologies that use a filter material. Settlers can also be installed as stormwater retention tanks to remove a portion of the organic solids that otherwise would be directly discharged into the environment.
To prevent the release of odorous gases, frequent sludge removal is necessary. Sludge and scum must be handled with care as they contain high levels of pathogenic organisms; they require further treatment and adequate disposal. Appropriate protective clothing is necessary for workers who may come in contact with the effluent, scum or sludge.
Operation & Maintenance
In settlers that are not designed for anaerobic processes, regular sludge removal is necessary to prevent septic conditions and the build-up and release of gas which can hamper the sedimentation process by re-suspending part of the settled solids. Sludge transported to the surface by gas bubbles is difficult to remove and may pass to the next treatment stage.
EPA (Editor) (1997): Wastewater Treatment Manuals – Primary, Secondary and Tertiary Treatment. Wexford: Environmental Protection Agency (EPA). URL [Accessed: 28.08.2014]. PDF
BALASUBRAMANIYAM, U.; ZISENGWE, L.S.; MERIGGI, N.; BUYSMAN, E. (2008): Biogas Production in Climates with long cold Winters. Wageningen: Wageningen University . URL [Accessed: 20.04.2010]. PDF
This study analyses the feasibility and potential production of biogas in countries with a cold climate, with emphasis on Romania, Kyrgyzstan, Georgia, Kazakhstan and Armenia. The results are compared with China, Nepal and Bolivia. The study also carefully reviews existing literature before suggesting the same technology for the colder target communities. It also contains recommendations on whether to use the plants on household or community level afterwards.
GTZ (Editor) (2007): Feasability Study for a National Domestic Biogas Programme in Burkina Faso. German Technical Cooperation (GTZ) GmbH. URL [Accessed: 21.04.2010]. PDF
This feasibility study resumes the current situation in Burkina Faso regarding social aspects, water and energy issues, agricultural and livestock sector activities, sanitation and environmental topics. It analyses the technical feasibility of currently available biogas digester designs for standardization and massive dissemination in the context of Burkina Faso. Also an outline of a National Domestic Biogas Programme is presented.
This document provides an overview and introduction on biogas sanitation (anaerobic digestion) for blackwater or for brown water, or excreta treatment for reuse in developing countries. The main technologies discussed are biogas settlers (BSs), biogas septic tanks, anaerobic baffled reactor (ABRs), anaerobic filter (AFs) and upflow anaerobic sludge blanket reactors (UASBs).
PETER-FROEHLICH, A.; BONHOMME, A.; OLDENBURG, M. (2007): Sanitation Concepts for Separate Treatment of Urine, Faeces and Greywater (SCST) – Results. EU-Demonstration project. PDF
Report of a European project with the objective to develop new sustainable sanitation concepts that have significant ecological and economic advantages compared to conventional end-of-pipe-systems. For this purpose, a demonstration plant was constructed and analysed in order to generate experiences on design, installation and operation.
D’AMATO, V. (2010): Webinar on Decentralized Wastewater Treatment Systems: Processes, Design, Management, and Use. November 23: Focus on Decentralized Wastewater System Design: Part 1. Conservation Technology Information Center, US Environmental Protection Agency (EPA), and Tetra Tech. URL [Accessed: 15.05.2014].
US EPA Webinar on decentralized wastewater management with presentations on technical systems such as septic tanks and grease traps.
http://www.youtube.com/ [Accessed: 01.05.2014]
This video with a virtual tour of a water resource recovery facility — commonly called a wastewater treatment plant — discusses how these facilities recycle the water and waste we flush down the drain. Water resource recovery facilities can also recover nutrients, generate energy, and create biosolids for use as fertilizer. This tour takes viewers through primary, secondary, and advanced treatment as well as the plant headworks and biosolids treatment process. It is developed by the Water Environment Federation and Gage 3D Studios (www.gage3d.com).
http://www.youtube.com/ [Accessed: 14.05.2014]
This video explains how to perform an activated sludge mixed liquor suspended solids settling test using a settlometer. This allows computing the settling abilities of the wastewater.
http://www.youtube.com/ [Accessed: 14.05.2014]
This video shows the wastewater (Primary Clarifier) math demonstration.
This video explains basics of clarifiers, the designing and state point analysis.
http://www.fao.org/docrep/T0541E/T0541E00.htm [Accessed: 26.04.2010]
This review is intended to up-date students, practitioners and consultants concerned with Biogas technologies, and to contribute to bringing biogas systems to a more advanced stage, and thereby to achieve a palpable impact in developing countries. Technical, social, environmental ad economic issues are addressed.